1. Before installation, it is not allowed to tear or op […]
1. Before installation, it is not allowed to tear or open the packaging bag or packaging film by hand; it should be stored strictly in accordance with the orientation standard marked on the packaging box; during the handling process, it should be handled with care and handled to avoid severe vibration and collision. You cannot force loading and unloading.
2. The installation direction must be correct: when the corrugated plate combination filter is installed vertically, the corrugated plate must be perpendicular to the ground; the connection between the filter and the frame in the vertical direction is strictly prohibited from leakage, deformation, damage, and glue leakage. After installation, the inner wall must be clean and free of floating dust, oil, rust and debris.
3. Before installing a partitionless high efficiency filter, the clean room must be thoroughly cleaned and wiped. If there is dust in the purifying air-conditioning system, it should be cleaned and wiped again. The small details that should be paid attention to meet the cleaning requirements. If the high efficiency filter is installed in the technical mezzanine or suspended ceiling, the technical layer or suspended ceiling should also be thoroughly cleaned and wiped.
4. Before installing the high efficiency filter, the package must be unpacked at the installation site for visual inspection.